2. As there was no flow of water, the water in the boiler got reduced, reducing the effectiveness of the boiler to cool the water in the primary circuit. Unfortunately, the dry steam blocked the movement of water in the water level indicator because anbsp;...
|Title||:||Profitable Management for the Subcontractor|
|Author||:||Robert L. Teets|
|Publisher||:||Tata McGraw-Hill Education - 1976-01-01|