Parts 1 and 2 have discussed the procedure for determining individual outlets ... and provision for future increase. Adding the circuits limited in other ways (heavy duty branch circuits, convenience outlet circuits, etc.) ... Usually this occurs when the distance from the panelboard to the first outlet is more than 100 feet. The basicanbsp;...
|Title||:||Handbook of interior wiring design|
|Author||:||Industry Committee on Interior Wiring Design|