electrode conductor be used to connect the service equipment enclosure to the grounding electrode. ... The connection to the building frame would have to be through a copper, aluminum, or copper-clad aluminum wire bonded to the service equipment and to the building ... The bonding jumper must be no smaller than the size required by Table 250-94 of the Code. ... the hot wires of the service shall be not smaller than 100 amp., if there are six or more 2- wire branch circuits, or if theanbsp;...
|Title||:||A 1987 national electric code|